Please read the following carefully before construction to ensure your installation goes smoothly
The installation manual of our company's concealed sensor urinal flusher describes the installation methods of several different panel products. Please install according to the panel styles of the products you choose and compare with the installation methods described in the manual.。
Thank you Wisdom for choosing our sensor urinal flusher. I believe you will be infinitely gratified after purchasing. From now on, you will become a guest of our company, and we will provide you with quality service at any time. In order to ensure that this product can give full play to its unique performance and extend its service life, our company advises you:
Please read the following before use to ensure that you can use this product normally.
一、Product functions and features
The company's sensor urinal flusher is carefully designed with infrared sensor principle, which brings together high-tech quality. it has:
1. Intelligence: automatic induction, can distinguish whether people need to use a urinal and make a judgment to flush.
2. Automatic: the user can flush the water automatically without any action within the sensing range of the urinal flusher.
3. Hygiene: hands do not need to be close to the appliance to flush the toilet, which is convenient and hygienic, and effectively eliminates cross-infection of bacteria.
4. Applicability: The product has beautiful appearance, simple and convenient installation, and is suitable for all kinds of new construction sites and modification of old projects.
二、Product performance parameters
|model||Communication type||DC type|
|Water supply caliber||G1/2'||G1/2'|
|Applicable water pressure||0.05~0.8MPa||0.05~0.8MPa|
|voltage||AC 220V/50Hz||DC 6V|
|Power consumption||Standby: <3W; Work: <5W||Standby： <0. 5mW|
|Power consumption||Induction for more than 3 seconds to start the device||Induction for more than 3 seconds to start the device|
|Flush time||Front part: 3 seconds Back part: 9 seconds (Adjustable from 3 to 15 seconds later)|||Front part: 3 seconds Back part: 9 seconds|
|Sensing distance||Factory setting 60cm (adjustable within the range of 30~80cm, subject to 297mm whiteboard test)|
三、Instructions for use
When the user stands in front of the urinal in a habitual manner for convenience, the first pre-wash flush will start after 3 seconds. When the user leaves, the internal computer memory system of the flusher will perform the second flush. When the urinal flusher is not used within 24 hours, the internal computer memory system will automatically flush once.
(二)Precautions for use
1. In order to avoid the possibility of failure, please do not install the product on stainless steel walls, other high-intensity reflective surfaces or other infrared sensors.
2. If there is dirt on the sensor window (ie, electric eye), please clean it up in time to avoid affecting the use effect.
3. If you find that the induction effect is not good during use, you can adjust the adjustable potentiometer on the main control board (see 4: Function Adjustment for details).
4. If you find that the amount of flushing water is insufficient during use, please clean the filter.
5. If you find that the AC-type urinal flusher has no induction or poor power connection, please turn off the power immediately and seek repairs from related professionals to avoid electric shock or other accidents.
(三)After the dry battery of type B product is used up, the dry battery must be replaced (as shown in the figure below)
六、Simple fault analysis and troubleshooting
When the following phenomenon occurs in the appliance, it may not be caused by the failure of the appliance. Please analyze and eliminate it according to the following table。
|phenomenon||the reason||Check analysis||exclude|
|No water||(1)Abnormal power supply||Check if there is normal power supply to the sensor||AC type: connect to power
DC type: replace the battery
|(2)Abnormal water supply||Check water source||Turn on the water supply system|
|(3)Connector poor contact||Is it loose||Reinsert|
|(4)The sensing distance is adjusted too large||Whether to adjust||Adjust potentiometer counterclockwise|
|(5)Filter clogged||Cleaning the filter|
|Non-stop water flow||Foreign matter on the solenoid valve film||Cleaning film|
|Little water||(1)Filter clogged||Cleaning the filter|
|(2)The regulating valve is adjusted too small||Anti-clockwise adjusting valve|