Please read the following carefully before construction to ensure your installation goes smoothly
The installation manual of the company's concealed induction squat toilet flusher describes the installation methods of several different panels. Please install according to the panel styles of the products you choose and contrast the installation methods described in the manual.
Thank you Wisdom for choosing our sensor squat toilet flusher. I believe you will be infinitely gratified after purchasing. From now on, you will become a guest of our company, and we will provide you with high-quality services at any time. In order to ensure that this product can give full play to its unique performance and extend its service life, our company advises you:
Please read the following before use to ensure that you can use this product normally.
一.Product functions and features
The company's sensor squatting toilet flusher is meticulously designed using the principle of infrared induction, which brings together high-tech quality. it has:
1. Intelligence: automatic induction, can distinguish whether people need to use the toilet and make a judgment to flush.
2. Automatic: the user can automatically flush the water without any action within the sensing range of the squat toilet flusher.
3. Hygiene: The hand does not need to be close to the appliance to flush the toilet, which is convenient and hygienic, and effectively eliminates the cross infection of bacteria.
4. Applicability: The product has beautiful appearance, simple and convenient installation, and is suitable for all kinds of new construction sites and modification of old projects.
二.Product performance parameters
|model||Communication type||DC type|
|Applicable water pressure||0.3-0.8MPa||0.3-0.8MPa|
|Applicable water temperature||50°C||50°C|
|voltage||AC 220V/50Hz||DC 6V|
|Power consumption||Standby: ≤3W; Working: ≤5W||Standby:≤0. 5mW|
|Induction time||Induction for more than 3 seconds, and enter the pre-rinsing state||Induction for more than 3 seconds to enter the pre-rinsing state|
|Flush time||Flush for 10 seconds (adjustable within 3-15 seconds)||Flush for 6 seconds within 2 minutes after induction, and flush for 10 seconds over 2 minutes|
|Sensing distance||Factory setting 60cm (adjustable within the range of 30-80cm, subject to 297mm297mm whiteboard test)|
三.Instructions for use
When the user squats in front of the toilet in a customary way, the flusher will activate the function of automatically distinguishing whether to use the appliance. When the squatting toilet flusher is determined to be used, it will enter the pre-flushing state after 3 seconds. When the user leaves The internal computer memory system of the flusher performs cleaning and flushing. When the squatting toilet flusher is not used within 24 hours, the internal computer memory system will automatically flush once.
(二)Precautions for use
1. In order to avoid the possibility of failure, please do not install the product on stainless steel walls, other high-intensity reflective surfaces or other infrared sensors.
2. If there is dirt on the sensor window (ie, electric eye), please clean it up in time to avoid affecting the use effect.
3. If you find that the induction effect is not good during use, you can adjust the adjustable potentiometer on the main control board (see 4: Function Adjustment for details)
4. If you find that the flushing water is insufficient during use, please clean the filter.
5. If you find that the AC-type squatting toilet flusher has no induction or poor power connection, please turn off the power immediately and seek repair by related professionals to avoid electric shock or other accidents.
In contrast to the panel installation method, after the panel is removed, the sensor distance is adjusted and the flush time is adjusted.
六.Simple fault analysis and troubleshooting
When the following phenomena occur in the appliance, it may not be caused by the failure of the appliance. Please analyze and eliminate it as described in the following table.
|phenomenon||the reason||Check analysis||exclude|
|No water||(1)Abnormal power supply||Check if there is normal power supply to the sensor||AC type: connect to power
DC type: replace the battery
|(2)Abnormal water supply||Check water source||Turn on the water supply system|
|(3)Connector poor contact||Is it loose||Reinsert|
|(4)The sensing distance is adjusted too large||Whether to adjust||Adjust potentiometer counterclockwise|
|(5)Filter clogged||Cleaning the filter|
|Non-stop water flow||Foreign matter on the solenoid valve film||Cleaning film|
|Little water||(1)Filter clogged||Cleaning the filter|
|(2)The regulating valve is adjusted too small||Anti-clockwise adjusting valve|
Address: No. 10, Donggang 3rd Road, Qujiang District, Quzhou City, Zhejiang Province
Business Hotline: +86-570-3853237
Service Hotline: 400-826-9218